Updating the database of the Illinois Compiled Statutes (ILCS) is an ongoing process.
Recent laws may not yet be included in the ILCS database, but they are found on this site as Public
soon after they become law. For information concerning the relationship between statutes and Public Acts, refer to the
Because the statute database is maintained primarily for legislative drafting purposes,
statutory changes are sometimes included in the statute database before they take effect.
If the source note at the end of a Section of the statutes includes a Public Act that has
not yet taken effect, the version of the law that is currently in effect may have already
been removed from the database and you should refer to that Public Act to see the changes
made to the current law.
(105 ILCS 5/34-18.49)
Carbon monoxide alarm required.
(a) In this Section:
"Approved carbon monoxide alarm" and "alarm" have the meaning ascribed to those terms in the Carbon Monoxide Alarm Detector Act.
"Carbon monoxide detector" and "detector" mean a device having a sensor that responds to carbon monoxide gas and that is connected to an alarm control unit and approved in accordance with rules adopted by the State Fire Marshal.
(b) The board shall require that each school under its authority be equipped with approved carbon monoxide alarms or carbon monoxide detectors. The alarms must be powered as follows:
(1) For a school designed before January 1, 2016 (the
effective date of Public Act 99-470), alarms powered by batteries are permitted. Alarms permanently powered by the building's electrical system and monitored by any required fire alarm system are also permitted.
(2) For a school designed on or after January 1, 2016
(the effective date of Public Act 99-470), alarms must be permanently powered by the building's electrical system or be an approved carbon monoxide detection system. An installation required in this subdivision (2) must be monitored by any required fire alarm system.
Alarms or detectors must be located within 20 feet of a carbon monoxide emitting device. Alarms or detectors must be in operating condition and be inspected annually. A school is exempt from the requirements of this Section if it does not have or is not close to any sources of carbon monoxide. A school must require plans, protocols, and procedures in response to the activation of a carbon monoxide alarm or carbon monoxide detection system.
(Source: P.A. 99-470, eff. 1-1-16; 100-201, eff. 8-18-17.)