TITLE 41: FIRE PROTECTION
CHAPTER I: OFFICE OF THE STATE FIRE MARSHAL
PART 175 TECHNICAL REQUIREMENTS FOR UNDERGROUND STORAGE TANKS AND THE STORAGE, TRANSPORTATION, SALE AND USE OF PETROLEUM AND OTHER REGULATED SUBSTANCES
SECTION 175.230 FLEET VEHICLE MOTOR FUEL DISPENSING FACILITIES
Section 175.230 Fleet Vehicle Motor Fuel Dispensing Facilities
Fleet vehicle motor fuel dispensing facilities shall comply with all of the requirements for unattended self-service motor fuel dispensing facilities in Section 175.220, except that the signs required under Section 175.220(a) and the fire detection and fire suppression systems required under Section 175.220(h) shall not be required. Fleet facilities shall comply with requirements for portable fire extinguishers found in Section 175.220(h)(2)(E) and 41 Ill. Adm. Code 174.350. Other signage requirements under Section 175.220 (for example, that emergency shutoffs be conspicuously marked) shall still apply, along with the remainder of the requirements of Section 175.220.